Join Date: Sep 2018
Location: Cape Elizabeth, Maine
Mentioned: 0 Post(s)
Tagged: 0 Thread(s)
Quoted: 26 Post(s)
Looking at the wiring diagram, I'm going to guess that the red and black go to the two lugs on the terminal strip and the two whites both go to the ground lug above the terminal strip (bonded neutral). The wiring to the panel should join up with the three of them there.
When the generator is running, confirm 240V between red and black and 120V between them and the whites before hooking them up that way.
Last edited by tabora; 04-14-2019 at 03:32 PM.